PREPARATION FOR MOVEMENT AND STORAGE. - Continued
Preparing Shelter for Movement. - Continued
(28) Install and secure the air conditioner covers.
(29) Close and secure shelter door.
(30) Cover all shelter apertures with pressure sensitive tape.
(31) Stow and secure ladder.
(32) Apply a preservative compound (item 29, app E) to all unfinished metal surfaces of the various pieces
of equipment when shelter is to be stored for an extended period of time.
DEATH or serious injury could result if electrical precautions are not taken when
maintaining this equipment.
Be sure that power cables are unplugged/
disconnected, that circuit breakers are set to OFF and that generator cables are
unplugged/disconnected. Be sure that the generator/commercial power system is
properly grounded. Always have another person standing by who is familiar with
electrical shock first aid.
Set all equipment and shelter power switches to the off or neutral position.
Set all circuit breakers in the main power service box to OFF.
When used in conjunction with Modular Print System, to ensure safety of
operator, power to circuit breaker is controlled by Module C supervisor.
Set commercial power breaker to OFF or shut down the 60 kW power plant in accordance with TM 5-
6115-594-14&P or TM 5-6115-625-14&P.
Disconnect the main power cable from the generator power source.
Disconnect the cable from the main power receptacle.