ASSEMBLY AND PREPARATION FOR USE. - Continued
Setting Up 15 KW Generator and Connecting Main Power Cable.
DEATH or serious injury could result if electrical precautions are not taken when
maintaining this equipment.
Be sure that power cables are unplugged/
disconnected, that circuit breakers are set to OFF and that generator cables are
unplugged/disconnected. Be sure the equipment is properly grounded. Always
have another person standing by who is familiar with electrical shock first aid.
Setting Up Generator.
Set all circuit breakers in main power service box to OFF.
Install ground rod and connect ground wire to ground rod and shelter grounding point.
(c) Refer to generator technical manual TM 5-6115-464-12 for instruction on installation and
operation of the generator.
When used in conjunction with Modular Print System, only the Module C
supervisor is authorized to operate controls on the Power Distribution Box.
Failure to follow these procedures can cause serious injury or DEATH.
(d) Connecting Main Power Cable to Shelter. Connect the 50 foot main power cable to the input
power receptacle located near door of shelter prior to connecting cable to power source. Connect 6 foot pigtail connector
to 50 foot power cable.
The cable connector and receptacle are keyed to ensure proper connection.