3-3. GENERAL. - Continued
TEST OR INSPECTION
1. NO ELECTRICAL POWER TO SHELTER SYSTEM.
The 15 KW generator must be shut down or the main circuit breaker on power distribution
box must be in the OFF position before connecting main power cable. Failure to do so
may result in DEATH or serious injury.
When used with the Modular Printing System, to ensure safety of operator, only the
Module C supervisor is authorized to operate controls of the power distribution box.
Connect the primary power cable to the input power receptacle located near the door of the
shelter. The cable connector and the receptacles are keyed to ensure proper connection.
Step 1. Check that the main power cable is correctly connected at main power receptacle.
Step 2. When used with the Modular Printing System, check to see if the main power cable is properly connected
at power distribution box. Request Module C supervisor verily connection and operation of the power
Step 3. Inspect to see that the generator is operating properly.
Start the 15 KW power plant in accordance with TM 5-6115-464-14&P or TM 5-6115-625-14&P