2-13. ASSEMBLY AND PREPARATION FOR USE. -Continued
Remove cover and refer to TM 5-3610-299-12&P, Paper Cutter Operation and Maintenance manual for
setup instructions for the paper cutter.
Connecting Power to Shelter and Power Distribution Box.
Remove power distribution box from storage location next to islatrol control box and position in accordance
with Figure 2-11 site layout.
Remove power cables from storage under air conditioners.
Do not set main circuit breaker CB1 power distribution box to ON position until all shelters have been properly
connected to the power distribution box. Module C supervisor is the only person authorized to set main circuit
breaker CB1 on power distribution box to ON position. Failure to do so may result in DEATH or serious injury.
Make sure that the main circuit breaker in the Power Distribution Box is in the OFF position before connecting
the power cable to the Distribution Box or Shelter. Failure to do so may result in electrical short and damage to
The generator operator will connect the main power cable from the generator set to the Power Distribution Box
Install grounding rod. Connect grounding rod wire to lug (1) on power input panel of the shelter. (Refer to
Figure 2-14 for location of grounding rod wire lug.)
Set main circuit breaker CB1 (1) on the Power Distribution Box in the OFF position. (Refer to Figure 2-15
for location of controls and indicators on Power Distribution Box.)
Connect power cable to the Finishing Section receptacle (2) on the Power Distribution Box. (Refer to
Figure 2-15 for location of receptacle.)