2-13. ASSEMBLY AND PREPARATION FOR USE. -Continued
Connect power cable to Finishing Section Receptacle (2) on the power input panel of the shelter. (Refer to
Figure 2-14 for location of receptacle.)
Request generator operator to energize power source.
Do not set main circuit breaker CB1 to ON if voltage is below 110 Vac or above 120 Vac on each phase
(A, B, or C).
Do not set main circuit breaker CB1 to ON if incorrect phase lamp lights on any phase. Do not set main
circuit breaker CB1 to ON unless frequency is 60 ± 1.0 Hz on each phase.
Damage to equipment will result if the above items are not within tolerance. Notify generator operator.
Read voltmeter (3) on Power Distribution Box control panel. Voltmeter must read between 110 and 120
Vac on phases A, B, and C. (Refer to Figure 2-15 for location of controls and indicators on Power
Figure 2-14. Power Cable Connections to Finishing