DIRECT SUPPORT TROUBLESHOOTING. - Continued
Table 5-1. Direct Support Troubleshooting - Continued
TEST OR INSPECTION
CIRCUIT BREAKER WILL NOT REMAIN IN ON POSITION.
Inspect the component served by the circuit breaker concerned for electrical defects in accordance
with the applicable commercial manual.
If necessary, rectify any defects in accordance with the applicable commercial manual.
Inspect breaker involved for failure.
If necessary, replace circuit breaker as described in paragraph 5-12.