EQUIPMENT RECEPTACLES ASSEMBLY. - Continued
Check shelter wall equipment receptacles for loose connections and excessive wear.
Inspect equipment receptacles covers for secure mounting.
DEATH or serious injury could result if electrical precautions are not taken when
maintaining this equipment. Be sure that circuit breakers are set to OFF. Be sure the
equipment is properly grounded. Always have another person standing by who is
familiar with electrical shock first aid.
Remove equipment receptacle screw (1) and cover (2).
Remove equipment receptacle screws (3).
Pull receptacle (4) from conduit.
Tag wall receptacle wires (5) and disconnect.
Remove receptacle (4).
Connect wires (5) to equipment receptacles (4) and remove tags.
Position in conduit.
Install screws (3) in equipment receptacle.
Install cover (2) on equipment receptacle and secure with screw (1).