2-14. ASSEMBLY AND PREPARATION FOR USE. - Continued
Figure 2-16. Power Cable Connections to Press Section Shelter
Read voltage meter (3, Figure 2-17) on phase monitor meter. Voltage must read between 110 and 120
Vac on phases A, B, and C.
Push down test phase switch (4). Correct phase lamp (5) should light.
Read frequency meter (6). Frequency must read 60 ± 1.0 Hz on phases A, B, and C.
Place all circuit breakers and switches on the Power Distribution Panel inside the shelter in the ON
Install flexible duct between air conditioner assembly vent and rear shelter wall.