Table 4-2. Troubleshooting ( Contd)
Test or Inspection
SHELTER SYSTEM AND COMPONENTS
If necessary, position LIGHTS circuit breaker in service box to on.
4. NO POWER AT ONE OR MORE EQUIPMENT RECEPTACLES
Step 1. Inspect the main power service box for applicable RECEPTACLES circuit breaker position to off.
If necessary, position applicable RECEPTACLES circuit breaker in service box to on.
Step 2. Inspect for defective receptacle or faulty wire connections as follows:
a. Position applicable RECEPTACLES circuit breaker in main power service box to off.
b. Remove three screws which attach receptacle cover to conduit box. (See fig. 4-5.)
Figure 4-5. Equipment Receptacle.