Table 5-1. Troubleshooting
TEST OR INSPECTION
SHELTER SYSTEM COMPONENTS (Con't)
6. UNABLE TO MAKE TELEPHONE CONNECTION WITH OTHER UNITS OF THE SPECIAL WARFARE PRINTING
Inspect for one or more defective telephone binding posts. If necessary, replace defective binding posts as
described in paragraph 14-2.
7. NO ELECTRICAL POWER TO SHELTER SYSTEM.
Step1. Inspect for generator set power source not operatin g. Start the generator set in accordance with the
applicable Department of the Army Technical Manual
Step 2. Inspect for circuit breakers not positioned to on. Position applicable circuit breakers to on.
Step 3. Check that main power cable is correctly connected at main power receptacle. (See fig. 5-1.)