Table 4-2. Troubleshooting (Con't)
Test or Inspection
Remove the two capscrews that secure the switch in the switchbox, and pull the defective switch
from the switchbox.
Tag and disconnect the wires from the switch.
Connect the wires to the replacement switch and remove the tags.
Install the switch in the switchbox and secure it in the switchbox with two capscrews.
Install the switchbox cover on the switchbox and secure it with two screws.
Position the LIGHTS circuit breaker to the ON position.
Step 3. Inspect the main power service box for LIGHTS circuit breaker positioned to off.
If necessary position LIGHTS circuit breaker in service box to on.
5. NO POWER AT ONE OR MORE EQUIPMENT RECEPTACLES.
Inspect the main power service box for applicable RECEPTACLES circuit breaker position to off.
If necessary, position applicable RECEPTACLES circuit breaker in service box to on.
Inspect for defective receptacle or faulty wire connections as follows: a. Position applicable
Figure 4-6. Equipment Receptacles, Removal and Installation
Pull receptacle from conduit box and inspect receptacle and wiring connections.
If necessary, replace defective receptacle and secure wiring connections as follows.
Tag and disconnect wires and remove receptacle.
Remove tags and connect wires to new receptacle.
Insert receptacle into conduit.
Position receptacle cover and secure with screws.
Position applicable RECEPTACLES circuit breaker in main power service box to on.